Last updated on JUNE 13, 2016
Applies to:Oracle Utilities Network Management System - Version 126.96.36.199 to 188.8.131.52 [Release 1.12]
Oracle Network Management for Utilities - DMS - Version 184.108.40.206 to 220.127.116.11 [Release 1.12]
Information in this document applies to any platform.
A digital or analog measurement was manually overridden via the SCADA Summary tool.
When the inhibit was cleared, the measurement may suddenly change to either an extremely large positive or negative value.
Sign In with your My Oracle Support account
Don't have a My Oracle Support account? Click to get started
Million Knowledge Articles and hundreds of Community platforms