When an "Inhibit" is Cleared on a SCADA Device,the Associated Digital and Analog Measurements May Suddenly Get Extremely Large or Small Values
Last updated on APRIL 23, 2018
Applies to:Oracle Utilities Network Management System - Version 22.214.171.124 to 126.96.36.199 [Release 1.12]
Oracle Network Management for Utilities - DMS - Version 188.8.131.52 to 184.108.40.206 [Release 1.12]
Information in this document applies to any platform.
A digital or analog measurement was manually overridden via the SCADA Summary tool.
When the inhibit was cleared, the measurement may suddenly change to either an extremely large positive or negative value.
Sign In with your My Oracle Support account
Don't have a My Oracle Support account? Click to get started
My Oracle Support provides customers with access to over a
Million Knowledge Articles and hundreds of Community platforms