When an "Inhibit" is Cleared on a SCADA Device,the Associated Digital and Analog Measurements May Suddenly Get Extremely Large or Small Values
(Doc ID 2147669.1)
Last updated on APRIL 23, 2018
Applies to:Oracle Utilities Network Management System - Version 126.96.36.199 to 188.8.131.52 [Release 1.12]
Oracle Network Management for Utilities - DMS - Version 184.108.40.206 to 220.127.116.11 [Release 1.12]
Information in this document applies to any platform.
A digital or analog measurement was manually overridden via the SCADA Summary tool.
When the inhibit was cleared, the measurement may suddenly change to either an extremely large positive or negative value.
To view full details, sign in with your My Oracle Support account.
Don't have a My Oracle Support account? Click to get started!