"FLISR Demand Scan" Does Not Take in to Account For Missing or Delayed SCADA Measurements
(Doc ID 2347327.1)
Last updated on MAY 07, 2018
Applies to:Oracle Utilities Network Management System - Version 18.104.22.168 to 22.214.171.124.0 [Release 1.12 to 2.3]
Oracle Network Management for Utilities - DMS - Version 126.96.36.199 to 188.8.131.52.0 [Release 1.12 to 2.3]
Information in this document applies to any platform.
A system had a couple of FLISR events in production where FLISR came up with wrong plan and tried to close into a fault.
Further investigation of this issue indicated that FLISR plan was incorrect due to the unavailability of some downstream fault indications during FLISR Demand Scan.
Those Fault indications came in after 2 minutes and FLISR did not consider them in its processing.
FLISR should consider indication from RTUs when they complete a success poll cycle. This particular system had SCADA points to indicate if an RTU has successfully completed its poll cycle.
FLISR must consider missing or delayed scada measurements when determining the plan.
To view full details, sign in with your My Oracle Support account.
Don't have a My Oracle Support account? Click to get started!
In this Document