Voltage Checks On RTUs For FLISR Automatic Mode
(Doc ID 2537789.1)
Last updated on OCTOBER 14, 2019
Applies to:Oracle Utilities Network Management System - Version 22.214.171.124.0 and later
Oracle Network Management for Utilities - DMS - Version 126.96.36.199.0 and later
Information in this document applies to any platform.
On : 188.8.131.52.0 version,
Voltage Checks on RTUs for FLISR Automatic Mode
Project has requested to add following additional checks before processing FLISR operation in automatic mode:
1. Faulted device tripped and an RDO is created on a Feeder in Automatic FLISR Mode
2. FLISR should Scan all the RTUs of the faulted feeder and check for Voltage Measurements-
a. IF Voltage Measurements are not present ( for example points not added on RTUs), FLISR will demote to Manual Mode
b. IF Voltage Measurements are present and above the configured MIN_VOLTAGE threshold, FLISR will abort
c. IF Voltage Measurements are present and below the configured MIN_VOLTAGE threshold, FLISR will continue its processing in Automatic Mode.
To view full details, sign in with your My Oracle Support account.
Don't have a My Oracle Support account? Click to get started!
In this Document