When Performing a Feeder Focus on Network Protectors in the Viewer, the Results are Inconsistent
(Doc ID 2644772.1)
Last updated on MARCH 02, 2020
Applies to:Oracle Utilities Network Management System - Version 18.104.22.168.0 to 22.214.171.124.0 [Release 2.3 to 2.4]
Oracle Network Management for Utilities - DMS - Version 126.96.36.199.0 to 188.8.131.52.0 [Release 2.3 to 2.4]
Information in this document applies to any platform.
On : 184.108.40.206.0 version, Web Workspace
In a specific area in the network model, network protectors are on the downstream side of distribution transformers, and they have parallel feeders feeding into a secondary network with Network protectors for each of the feeders.
When the Network protector device is directly downstream of a distribution transformer, the secondary network is included in the Feeder Focus trace results.
However, when the NP device is NOT directly downstream (i.e. directly downstream of the distribution transformer is a zero-impedence conductor and THEN the NP device is attached to that conductor), the region is not included in the trace results.
To view full details, sign in with your My Oracle Support account.
Don't have a My Oracle Support account? Click to get started!
In this Document